Requirements to connect an M-bus equipment to the Box/Hub
The Mbus bus is a serial bus powered by the master (Box or Hub) with 37V, the Box/Hub can handle natively 3.6mA (3*UL) on the bus.
Note: Be sure to check this information on your targeted bus, otherwise it will not work correctly.
Connect a Mbus equipment
To connect correctly the Box/Hub on the bus, you will have to check the address of all the types of equipment on the network and pick an available one for the Box/HUB.
Then in your configuration Tool, you should be able to fill in the required parameters:
NB: Sometimes, you will meet types of equipment using a secondary address, we will be compliant with this setup very soon
Read a property in a Mbus equipment
To read a property in a M-bus equipment, you'll have to know two required pieces of information.
For each properties:
- DIF + DIFE
- DIF + DIFE length
- VIF + VIFE
- VIF + VIFE length
*DIF: Data Information Field
*DIFE: Data Information Field Extension
*VIF: Value Information Field
*VIFE: Value Information Field Extension
Requirements to connect an LPB equipement to the Box/Hub
Here is a view of the parameters you will need to fill in order to create your LPB equipment: Network requirements: First of all, you'll need information for your Box/Hub: -> An available segment number and Device number The default parameters that ...
Requirements to connect a KNX LTE equipement to the Box/Hub
In order to connect a Box/Hub to a KNX LTE equipment you'll need to: -> Add the Box/Hub correctly in the KNX LTE network -> Collect the required equipment information in order to read data. Box/Hub network configuration: To correctly add the Box/Hub ...
Requirements to connect a LoRaWAN device to the Box/HUB
In order to connect your Lorawan device to our Box/HUB you'll need to have in mind these informations: 1. If your Lorawan device is not in our compatibility checker that means that we don't have the associated codec. -> You will have ...
Bulk creation for LoRaWAN equipment
You can now add multiple LoRaWAN types of equipment at once. This feature is only available on the web console. To add equipment, access the bulk creation mode by going through these steps: Import a CSV file with at least the following info: ...
Checklist to install a Wattsense Box in a Modbus IP and RS485 network
Modbus IP RTU Slave address* of all equipment If applicable R IP address of all equipment R N/A Modbus register list* (so-called exchange table) of all equipment R R Modbus UDP ports R N/A Network communication configuration (Baud rate/Parity/Data ...