Requirements to connect an LPB equipement to the Box/Hub
Here is a view of the parameters you will need to fill in order to create your LPB equipment:
First of all, you'll need information for your Box/Hub:
-> An available segment number and Device number
The default parameters that we recommend for the segment number is 2 and for the device number 16
In order to read data from equipment you'll have to fill these blanks:
In the previous example the equipment parameters would be:
-> Segment number: 1
-> Device number: 2 or 3
Here are the parameters that you'll need to fill if your equipment is not available in our database.
"Access Type" would be: READ ONLY or WRITE ONLY
For "Data Format" you'll have a list of our supported data format, you'll choose the one corresponding to your property.
Requirements to connect a KNX LTE equipement to the Box/Hub
In order to connect a Box/Hub to a KNX LTE equipment you'll need to: -> Add the Box/Hub correctly in the KNX LTE network -> Collect the required equipment information in order to read data. Box/Hub network configuration: To correctly add the Box/Hub ...
Requirements to connect a LoRaWAN device to the Box/HUB
In order to connect your Lorawan device to our Box/HUB you'll need to have in mind these informations: 1. If your Lorawan device is not in our compatibility checker that means that we don't have the associated codec. -> You will have ...
Requirements to connect an M-bus equipment to the Box/Hub
The Mbus bus is a serial bus powered by the master (Box or Hub) with 37V, the Box/Hub can handle natively 3.6mA (3*UL) on the bus. Note: Be sure to check this information on your targeted bus, otherwise it will not work correctly. Hardware ...
Checklist to install a Wattsense Box in a Modbus IP and RS485 network
Modbus IP RTU Slave address* of all equipment If applicable R IP address of all equipment R N/A Modbus register list* (so-called exchange table) of all equipment R R Modbus UDP ports R N/A Network communication configuration (Baud rate/Parity/Data ...
Troubleshooting LON IP network with the Wattsense box
This topic will give tips for troubleshooting a LON IP setup: Make sure the Wattsense Box has a static IP address configured. Go to Configuration -> Connectors (select the appropriate Ethernet port) Connect to the LON configured server and check the ...