Requirements to connect a KNX LTE equipement to the Box/Hub
In order to connect a Box/Hub to a KNX LTE equipment you'll need to:
-> Add the Box/Hub correctly in the KNX LTE network
-> Collect the required equipment information in order to read data.
Box/Hub network configuration:
To correctly add the Box/Hub in the KNX LTE network you'll have to assign a free and unique individual address and internal address (required by wattsense software design):
Ex: 0.2.15 and 0.2.16
In this case, the individual address would be either : 0.2.2 / 0.2.3 / 0.2.4
You'll be able to use our configuration wizard to generate all the properties we are currently supporting:
To do that you can select a Synco device present in the wizard configuration list:
(1) -> Go in "configuration" tab
(2) -> Add a new device using the wizard configuration tool and select one Synco
Requirements to connect an LPB equipement to the Box/Hub
Here is a view of the parameters you will need to fill in order to create your LPB equipment: Network requirements: First of all, you'll need information for your Box/Hub: -> An available segment number and Device number The default parameters that ...
Requirements to connect a LoRaWAN device to the Box/HUB
In order to connect your Lorawan device to our Box/HUB you'll need to have in mind these informations: 1. If your Lorawan device is not in our compatibility checker that means that we don't have the associated codec. -> You will have ...
Requirements to connect an M-bus equipment to the Box/Hub
The Mbus bus is a serial bus powered by the master (Box or Hub) with 37V, the Box/Hub can handle natively 3.6mA (3*UL) on the bus. Note: Be sure to check this information on your targeted bus, otherwise it will not work correctly. Hardware ...
Checklist to install a Wattsense Box in a Modbus IP and RS485 network
Modbus IP RTU Slave address* of all equipment If applicable R IP address of all equipment R N/A Modbus register list* (so-called exchange table) of all equipment R R Modbus UDP ports R N/A Network communication configuration (Baud rate/Parity/Data ...
Required open Port in a network for Box/Remote HUB (with sim card suspended)
The Box is not a server thus does not require to open ports in your internal network, The box communicates with remote servers, your firewall has to authorized communication with the box throught: *.wattsense.com, TCP port 443 (HTTPS) and 19000 ...